We at ALPS MSI has the software, instruments, equipment and skills to maintain if not improve motor efficiency. Vibration increases motor load as well as your operating cost. Let us (ALPS MSI) solve your problems and help you achieve peace of mind as we give importance in reducing your operating cost – this is the Value of you Money we can confidently offer.
To minimize 40% stator loss, its circular mil/ampere has to be restored based on EASA winding database. We invested on high-end technologies in forming coils, design software, skills and quality of raw materials (Class H).
ISO and ABMA Standards that we must consistently comply while in the process of repair, testing, and commissioning.
Our client experienced 5 – 15% energy conservation after rewinding.
Download our ABB Certificate here.
One of the biggest hospitals in Makati City experienced high vibrations and back-job from their service provider on motor rewinding. There were two motors with the following specification: 15HP, 230V/460V, 41/20.70 Amps, PF 83.3, 3Ph, 60Hz, RPM 3505. Although the motor was operational, we offered a minimum energy savings of 10% versus another unit.
Thanks to our Reliability Team who used power analyzer and OneProd Falcon Smart Condition Monitoring – vibration analyzer, we were able to determine its root cause and rectify. Rotor and impellers were dynamically balance and run the unit in accordance to EASA AR100 Table 4-5 Unfiltered Vibration Limits.